Apart from the regs associated with OSHA, this really is the decision of
=0Ayour local fire marshal.
Ronnie Houston, MS, HT(ASCP)QIHC=0DAnatomic Pathology Manager
Columbus Children's Hospital
700 Children's Drive
Columbus, OH 43205
(614) 722 5465
[mailto:email@example.com] On Behalf Of
Mitchell, Jeannette M.
=0ASent: Wednesday, May 30, 2007 6:36 AM
Subject: [Histonet] histology regs
Does anyone know what fire codes REALLY apply to histology labs and how
did one justify having a tissue processor in less than 500 square feet
without a fire barrier around it ?
The reason I ask is :
We have a 10x22' tissue processing workroom with 5 routine processors,
one recycling system,
and explosion cabinets containing xylene, toluene, and ethanol.
Overall we have approx=2E 70 gallons of etoh and solvents in this 220'
We have been told by an independent industrial hygienist that we should
only have 4.4 gallons (or 2 gallons per 100 square feet) of combustibles=0Din this room and each tissue processor should be separated from the=0Dother by "1 hour construction" (some type of barrier that would take an
hour to burn through) according to NFPA 99 Chapter 11.
=0AI have visited many histology labs in the New England area and I have
=0Anever seen tissue processors separated by 1 hour burn barriers or
processors in separate 500 sq. foot rooms (10 gallons of combustibles
=0Aper processor would require this space).
I have asked for a second opinion as this is not practical, rational, or
PLEASE share your experience with fire regs in your lab ~
Jude Carpenter, BS, HTL (ASCP)
Supervisor of Histology/Surgical Pathology/Autopsy
Fletcher Allen Healthcare
111 Colchester Ave.
Burlington, VT 05401
This message, and any attachments, may contain information that is
confidential, privileged, and/or protected from disclosure under state
and federal laws that deal with the privacy and security of medical
information. If you received this message in error or through
inappropriate means, please reply to this message to notify the Sender
that the message was received by you in error, and then permanently
delete this message from all storage media, without forwarding or
retaining a copy.
Histonet mailing list
Confidentiality Notice: This e-mail message, from Children'sHospital, Columbus, Ohio, including any attachments, is for thesole use of the intended recipient(s) and may contain confidentialand privileged information. The recipient is responsible tomaintain the confidentiality of this information and to use theinformation only for authorized purposes pursuant to Children's=0AHospital's confidentiality policies. If you are not the intendedrecipient (or authorized to receive information for the intendedrecipient), you are hereby notified that any review, use,disclosure, distribution, copying, printing, or action taken inreliance on the contents of this e-mail is strictly prohibited. Ifyou have received this communication in error, please notify usimmediately by reply e-mail and destroy all copies of the originalmessage. Thank you.
Histonet mailing list